I know you will need to desire to uncover out how intermatic switch performs and which can be best to purchase? Doesn’t it baffle your thoughts a little? Doesn’t it spark your curious mind, and make you believe incessantly about it? Are you currently considering studying facts, trivia as well as other exciting information regarding it? You might have come to the ideal location because every single so normally we update this web site with a variety of details about intermatic switch. you could study the product specifics and critiques as blelow,obtain the best to purchase having a discount price tag .
Reviews: customer reviews...
List Price: unavailable
Sale Price: Too low to display.
No description available.
No features available.
There was an error connecting to the Amazon web service, or no results were found for your query.
Do you really feel that the facts and facts which you have just read satisfies your curiosity about %keywords%? If that’s the case, send us a message of affirmation. Nonetheless, for those who truly feel that there’s a will need for improvement, please also let us know exactly where we are in a position to add a great deal much more specifics. It is our aim to create this website the leading resource for %keywords%. Your feedback is going to become really appreciated!
I've read the forums, but cannot find a solution to my particular configuration. I am trying to wire a timer switch for my patio lights, which has four wires (Load, Hot, Ground and Neutral). The original single pole switch is housed in a double box, with no neutral wires twisted at the back. Running neutral from the light source is not an ideal scenario. I'm wondering what the best way to configure the wiring without running the neutral, if in fact it is possible to do so. FYI, the other switch in the double box is a three-way on the same circuit, i.e. I have a red, black and white wire. Is there any way to connect the neutral to one of these? In light of Jim's reply, a clarification: I am not installing a countdown timer switch (i.e. turns off after a set amount of time); it is a programmable light-on/light-off switch for when I am out of town, for my outdoor lights.
And got the following answer:
Using a neutral from the 3 way would most likely create a code violation unless the wires are individual wires pulled into conduit, but the easy fix is without changing any wiring you can use an Intermatic EJ500 series http://www.amazon.com/gp/product/B000E8VAIO/ref=as_li_qf_sp_asin_tl?ie=UTF8&camp=211189&creative=373489&creativeASIN=B000E8VAIO&link_code=as3&tag=theurbhea08-20 , they are made to replace a standard single pole or 3-way, they use a battery for keeping time and don't use a neutral.