Here would be the primary points about close limit switch ,From here you can get the item details such as description,function ,price tag and a few other best associated products ,you can get the information that that is the best to buy and find the discount value.
if you need to study extra evaluations about close limit switch or relevant product,it is actually simple to click on the image and get a lot more information in regards to the items which you intriguing,if you want to buy the item ,you’ll need to read extra evaluations.
Reviews: customer reviews...
List Price: unavailable
Sale Price: Too low to display.
No description available.
No features available.
There was an error connecting to the Amazon web service, or no results were found for your query.
If you identified this post insightful, please let us know. It truly is your feedback that keeps us motivated to dig out the particulars. If you’ll find any other issues you’d prefer to see us addresses, once extra, just let us know and we will include things like them in future articles and newsletters.
This truly is your website. We cover the troubles about %keywords% that matter to you. Please bookmark our site and let your friends know about us.
spandicraft asked Does a high limit switch on a nat gas furnace have a 24v continuous current leading to it?
Currently my Furnace's 4 blinking lights has lead me to test the High limit switch which reads closed (0 ohms). However would I read voltage going to the switch if I tested either lead to ground? If so I think I may have a problem with my control board possibly because I don't show anything going to it. The other jumper switches test good also. Thanks in advance, Steve
And got the following answer:
It's a tricky question, and depends on the particulars of your furnace. In any case, I wouldn't expect to get anything to the high limit unless it was actively trying to ignite / heat. That being the case, I'd expect that yes, you should get 24v to / through it If the 4 "blinks" are leading you to the high limit switch, I'd first ask if you're sure you're testing the correct limit switch. There should be at least one high limit, a roll-out switch and possibly a vent spill switch. Roll-outs are sometimes manually reset, and vent spill switches are nearly always manually reset. (Tiny red pop-out button) The quick and easy way to test would be to simply pull the wires from the limit and put a jumper across them, guaranteeing that it remains a closed circuit, then power up the furnace, initiate a call for heat and see what happens. Give it a try and re-post. Hope this helps.