I know you should choose to find out how light switch timer intermatic operates and that is greatest to purchase? Does not it baffle your thoughts a bit? Doesn’t it spark your curious mind, and make you consider incessantly about it? Are you currently serious about studying details, trivia as well as other interesting information about it? You might have come towards the appropriate location since every so normally we update this web page with a variety of information regarding light switch timer intermatic. you may study the solution details and reviews as blelow,uncover the best to purchase using a discount price .
Reviews: customer reviews...
List Price: unavailable
Sale Price: Too low to display.
No description available.
No features available.
There was an error connecting to the Amazon web service, or no results were found for your query.
This is by far amongst the finest articles we have observed lately. We hope you enjoyed reading it. Every year it appears that somebody comes out applying a brand new take on an old trouble, nonetheless, this definitely would be the most interesting approach to have a look at it that we’ve positioned.
In case you might have some suggestions on %keywords% that you just simply would like to share with our other readers, please leave your comments. We would welcome your input into the discussion.
I've read the forums, but cannot find a solution to my particular configuration. I am trying to wire a timer switch for my patio lights, which has four wires (Load, Hot, Ground and Neutral). The original single pole switch is housed in a double box, with no neutral wires twisted at the back. Running neutral from the light source is not an ideal scenario. I'm wondering what the best way to configure the wiring without running the neutral, if in fact it is possible to do so. FYI, the other switch in the double box is a three-way on the same circuit, i.e. I have a red, black and white wire. Is there any way to connect the neutral to one of these? In light of Jim's reply, a clarification: I am not installing a countdown timer switch (i.e. turns off after a set amount of time); it is a programmable light-on/light-off switch for when I am out of town, for my outdoor lights.
And got the following answer:
Using a neutral from the 3 way would most likely create a code violation unless the wires are individual wires pulled into conduit, but the easy fix is without changing any wiring you can use an Intermatic EJ500 series http://www.amazon.com/gp/product/B000E8VAIO/ref=as_li_qf_sp_asin_tl?ie=UTF8&camp=211189&creative=373489&creativeASIN=B000E8VAIO&link_code=as3&tag=theurbhea08-20 , they are made to replace a standard single pole or 3-way, they use a battery for keeping time and don't use a neutral.