Hi! Now you might be check about intermatic light timer product where you are going to find the evaluations, videos, links and photos that will certainly spark your interest. This website give info that you just will have to have. There’s a entire array of sources that are waiting to become found. Please carry on reading and search more critiques or goods as under. We have exciting resources that have been gathered by our professionals in intermatic light timer .hope you will get the best reviews and acquire the right product about intermatic light timer.
Reviews: customer reviews...
List Price: unavailable
Sale Price: Too low to display.
No description available.
No features available.
There was an error connecting to the Amazon web service, or no results were found for your query.
What do you think of the %keywords% web web-site? Let us know your thoughts and comments by leaving a reply on our entries or by sending us an e-mail. We would enjoy to hear from you.
In case you really feel we missed an important update, let us know and we’ll be pleased to make a post!
I've read the forums, but cannot find a solution to my particular configuration. I am trying to wire a timer switch for my patio lights, which has four wires (Load, Hot, Ground and Neutral). The original single pole switch is housed in a double box, with no neutral wires twisted at the back. Running neutral from the light source is not an ideal scenario. I'm wondering what the best way to configure the wiring without running the neutral, if in fact it is possible to do so. FYI, the other switch in the double box is a three-way on the same circuit, i.e. I have a red, black and white wire. Is there any way to connect the neutral to one of these? In light of Jim's reply, a clarification: I am not installing a countdown timer switch (i.e. turns off after a set amount of time); it is a programmable light-on/light-off switch for when I am out of town, for my outdoor lights.
And got the following answer:
Using a neutral from the 3 way would most likely create a code violation unless the wires are individual wires pulled into conduit, but the easy fix is without changing any wiring you can use an Intermatic EJ500 series http://www.amazon.com/gp/product/B000E8VAIO/ref=as_li_qf_sp_asin_tl?ie=UTF8&camp=211189&creative=373489&creativeASIN=B000E8VAIO&link_code=as3&tag=theurbhea08-20 , they are made to replace a standard single pole or 3-way, they use a battery for keeping time and don't use a neutral.