The item beneath about intermatic light timers has gotten lots of interest, lots more than any other on our internet site. We believe it’s for the reason that it pulls no punches. However, while it is an important issue, it really is not all doom and gloom, there’s an additional point of view that some locate rather unorthodox, but workable.
This product short article has proven to be pretty helpful to our readers and so they come back frequently to keep abreast of your newest developments. When intermatic light timers remains a crucial topic, it is generally an added bonus when you may be enlightened, as well as amused by being shown the other side with the challenge. Some factors will not be normally what they appear.Study on for much more insight.”
Reviews: customer reviews...
List Price: unavailable
Sale Price: Too low to display.
No description available.
No features available.
There was an error connecting to the Amazon web service, or no results were found for your query.
If you might be getting any challenges accessing the feeds or updates inside the e-mail concerning our newest news about %keywords%, please truly feel free of charge of charge to let us know. We know you would prefer to develop into in the know so we’d delight in to assist you on that.
We also decide to hear any feedback from you to create our weblog greater. Leave a comment and inform your buddies and household about us! We’ll make absolutely everybody updated about %keywords%.
I've read the forums, but cannot find a solution to my particular configuration. I am trying to wire a timer switch for my patio lights, which has four wires (Load, Hot, Ground and Neutral). The original single pole switch is housed in a double box, with no neutral wires twisted at the back. Running neutral from the light source is not an ideal scenario. I'm wondering what the best way to configure the wiring without running the neutral, if in fact it is possible to do so. FYI, the other switch in the double box is a three-way on the same circuit, i.e. I have a red, black and white wire. Is there any way to connect the neutral to one of these? In light of Jim's reply, a clarification: I am not installing a countdown timer switch (i.e. turns off after a set amount of time); it is a programmable light-on/light-off switch for when I am out of town, for my outdoor lights.
And got the following answer:
Using a neutral from the 3 way would most likely create a code violation unless the wires are individual wires pulled into conduit, but the easy fix is without changing any wiring you can use an Intermatic EJ500 series http://www.amazon.com/gp/product/B000E8VAIO/ref=as_li_qf_sp_asin_tl?ie=UTF8&camp=211189&creative=373489&creativeASIN=B000E8VAIO&link_code=as3&tag=theurbhea08-20 , they are made to replace a standard single pole or 3-way, they use a battery for keeping time and don't use a neutral.