Below would be the information about industrial temperature switch ,From right here you may get the item specifics like description,feature ,price and some other greatest connected goods ,you will get the facts that which can be the ideal to purchase and come across the discount price.
if you would like to understand a lot more critiques about industrial temperature switch or other associated solution , it’s simple to click the image and get additional info about the solutions which you exciting,when you are interested the item ,you must study additional evaluations.
Reviews: customer reviews...
List Price: unavailable
Sale Price: Too low to display.
No description available.
No features available.
There was an error connecting to the Amazon web service, or no results were found for your query.
If you discovered the write-up beneficial, please pass on our information and facts for your buddies. Several with the difficulties discussed inside the write-up are not broadly identified.
When you would like substantially much more articles like this, please take some moments to provide us your feedback. Though %keywords% is normally discussed, access to information about it may be challenging to find. Please come back and have a look at us after again, we’ll have additional high excellent articles for the reading pleasure.
eagle asked At what point does a heat pump lose its efficiency and resistance heat become more efficient?
At what point below freezing does it become more efficient?
And got the following answer:
Depends on the working fluid they use , generally it's R-134a and that boils at -26 C so the closer outside temperature gets to that the slower the fluid boils and the less heat you get from the pump. Generally they set the pump to just switch over automatically to resistance heat at a predetermined temperature usually around freezing (32F or O deg C) If they use CO2 as a refrigerant fluid it boils at -109 F so even if outside temperatures get down to 20 F, in comparison that 20F looks downright balmy to liquid CO2 at -109 F. So in short , this heat pump would still be more than 100% efficient at this temperature so it would not switch to resistance heat until say around -25F temperatures were reached. But since CO2 operates at very high pressures, everything has to be built for high pressures which adds weight and a lot of cost to the system, so these are generally for industrial use So in short, the lower the temperature outside the more the efficiency of the heat pumps drop off. The reported 400% efficiency occurs at around 55F and drops off from there to 100 % when you close in that low temperature cut off I spoke of above. At 100% your tied with resistance heating so you might as well use that and not wear out the mechanical pump