Here are specifics about limit switch for furnace ,From here you are going to get the item particulars which include things like description,function ,price and some other very best related products ,you can get the particulars that which can be the appropriate to purchase and uncover the discount value.
when you will need to study more evaluations about limit switch for furnace or other related item,you can click the image and get far more info concerning the items that you just interesting,for anyone who is interested the solution,it’s essential to read much more critiques.
Reviews: customer reviews...
List Price: unavailable
Sale Price: Too low to display.
No description available.
No features available.
There was an error connecting to the Amazon web service, or no results were found for your query.
Did you find the post believed provoking? We unquestionably did, and so did a huge selection of our regular readers. It seems the much a lot more answers we uncover, the substantially much more queries which can be asked. By signing up for our newsletter you may be notified when we post our subsequent write-up on %keywords%. Join thousands like you and stay on very best in the most existing news since it is usually released!
spandicraft asked Does a high limit switch on a nat gas furnace have a 24v continuous current leading to it?
Currently my Furnace's 4 blinking lights has lead me to test the High limit switch which reads closed (0 ohms). However would I read voltage going to the switch if I tested either lead to ground? If so I think I may have a problem with my control board possibly because I don't show anything going to it. The other jumper switches test good also. Thanks in advance, Steve
And got the following answer:
It's a tricky question, and depends on the particulars of your furnace. In any case, I wouldn't expect to get anything to the high limit unless it was actively trying to ignite / heat. That being the case, I'd expect that yes, you should get 24v to / through it If the 4 "blinks" are leading you to the high limit switch, I'd first ask if you're sure you're testing the correct limit switch. There should be at least one high limit, a roll-out switch and possibly a vent spill switch. Roll-outs are sometimes manually reset, and vent spill switches are nearly always manually reset. (Tiny red pop-out button) The quick and easy way to test would be to simply pull the wires from the limit and put a jumper across them, guaranteeing that it remains a closed circuit, then power up the furnace, initiate a call for heat and see what happens. Give it a try and re-post. Hope this helps.