Below will be the most important points about din rail timer ,From right here you are going to get the solution facts including description,function ,price and a few other very best connected products ,you can get the particulars that that is the ideal to purchase and uncover the discount value.
when you may need to study much more reviews about din rail timer or relevant item , it is easy to click the picture and get far more information in regards to the items that you fascinating,for anyone who is interested the product ,you will need to read a lot more testimonials.
Reviews: customer reviews...
List Price: unavailable
Sale Price: Too low to display.
No description available.
No features available.
There was an error connecting to the Amazon web service, or no results were found for your query.
Do you really feel that the information and facts and facts which you have just read satisfies your curiosity about %keywords%? If that’s the case, send us a message of affirmation. Nevertheless, for those who genuinely really feel that there is a will require for improvement, please also let us know where we’re capable to add significantly extra specifics. It is actually our aim to make this web-site the top resource for %keywords%. Your feedback is going to become really appreciated!
hadi asked din rail relay with timer? exists?
Is there such a think as a DIN rail mountable relay with an OFF timer? IE, when the relay contacts are closed the relay switches the load on, but when the relay contacts are open the load will switch off after 10 seconds. I am looking for a relay that would take input and output at 220V and minimum 16A per switched load. Thanks for the help.
And got the following answer:
You want an "off delay" timer, perhaps something like this: http://uk.rs-online.com/web/0221092.html That was one of the first that I googled. I'm sure there are US products as well. An alternative is to use an off-delay timer that has a low current rating to control a contactor that has contacts with a higher current rating. That arrangement is easier to compile as there are oodles of off-delay timers that can't handle 16A, and there are oodles of contactors that can handle 16A but don't provide an off-delay function. Try googling off delay timer.